May 11, 1998
Weil-McLain Announces Recall to Repair Gas Boilers
Weil-McLain, of Michigan City, Ind., is recalling 8,500 Weil-McLain gas boilers for field adjustment of the gas control valve. These boilers' gas control valves, made by White-Rodgers, could have gas pressure settings that are too high. Incorrect gas pressure can cause the boiler to produce dangerous carbon monoxide, which can then leak, causing serious injury or death.
The Weil-McLain model GV gas boilers subject to this recall are equipped with certain White-Rodgers model 36C98-303 gas control valves with date codes 9621 through 9723. The date code and model number can be found on the unit's gas control valve, which is located at the front and center section of the boiler under the jacket. Also, all Weil-McLain GV boilers located at elevations more than 7,000 feet above sea level are being recalled. These boilers have "WEIL-McLAIN GOLD GV" written on the boiler jacket. Heating and cooling companies and contractors sold these boilers nationwide from June 1996 to November 1997 for about $1,500 to $3,000. Approximately 1,000 GV boilers were installed from June 1990 to January 1998 at locations above 7,000 feet elevation.
Consumers should immediately check to see if they have a Weil-McLain GV boiler affected by this recall. For assistance in checking the boiler's gas valve model and date code, or for other additional information, consumers should call Weil-McLain at (800) 625-5249 anytime. If a consumer has an affected boiler, Weil-McLain will arrange for a free adjustment of the gas control valves' pressure setting.